JP Fluid ControlHome Brass 2-Way Zone Valve
2 Way electric ball valve with G1-1/4 inch pipe threads and powerful and energy efficient 24V AC/DC actuator (max 20Nm). Media from -20 to 130°C, max pressure 32 bar at 20°C. Brass valve housing with hard chromed ball and PTFE valve seats. The nominal diameter is 32mm, the Kv-value is 100m3/h (1666.7 l/min water at dP=1 bar, water). 3-point control. Rotation 0-90° in only 4 sec. Compact and strong actuator housing (IP67) with position indicator. Manual override function and two extra limit switches for position feedback.
£ 211.98 (£ 256.50 tax incl.)
Instead of £ 211.98
Warning: Last items in stock!
This strong and energy efficient 2-way electrical ball valve from JP Fluid Control can be used to automatically shut of pipes with gas or fluids. The valve has 1-1/4 inch pipe threads (internal thread, BSPP). The housing of the valve is made of brass with a hard chrome plated brass ball and PTFE (teflon) seat rings. The actuator is suitable for both 24 volt AC 50/60Hz (alternating current) and 24 volt DC (direct current). With switches on the circuit board, the actuator can be set for AC or DC. The factory default setting is direct current (DC). It is very imortant to set the actuator to AC, before using a 24V AC power supply. The actuator has a robust aluminium housing (IP67, provided that an appropriate cable is connected) and delivers maximally 20 Nm torque. The valve rotates from 0 to 90 degrees in 4 seconds. When the ball reaches an end position, the electric motor is turned off and no energy is consumed. The actuator is equipped with two additional limit switches for position-feedback. The limit switches are positioned at 0 and 90 degrees. If required, the angular position of the switches can be adjusted by the user. A mechanical position indicator on the top of the actuator shows the valve position. The actuator is equipped with a manual override.
|Actuator ref:||AG-020-B||Ball Valve ref:||230B114|
|Voltage:||24V DC/AC (50/60Hz)||Housing:||Brass (CW 617N)|
|Nom./Max. Current:||0.2/1.2 A||Ball:||hard chrome plated brass|
|Protection:||IP67||Seat rings:||PTFE (teflon)|
|Duty Cycle:||S2 30min.||Pipe threads:||G1-1/4" BSP|
|Open/Close:||4 s||Nominal Diameter:||32mm (DN)|
|Amb. Temp.:||-10°C..50°C||Installation length:||91 mm|
|Range:||0-90°||Max pressure (@20°C):||32 bar|
|Extra limit switches:||2||Function:||2 way|
|Manual override:||Yes||Temp medium:||-20°C..130°C|
Dimensions of the AG-020-B actuator and 230B114 ball valve.
This valve can be used in combination with gases and fluids. Some examples of compatible media are water, (compressed) air, vacuum (max -0.9 bar), oils and fuels. The brass housing is not suitable for chloride solutions (like seawater, swimming pools) or demineralized water. The maximum pressure at room temperature is 32 bar, at higher temperatures the maximum allowed temperature decreases (see figure below). The direction of pressure is not important, the direction of flow may be in any direction. The temperature range of the medium lies between -20°C and 130°C. At high temperatures, it is recommended to install the valve in a ventilated area. It is allowed to install the valve in a humid environment provided that all parts, like an appropriate electrical cable, are correctly fixed. Ball valves can be used with light contaminated fluids. Some examples of applications for this valve are HVAC, irrigation, industrial automation, water management.
Maximum pressure as a function of temperature.
The actuator works with 24 volt DC and 24 volt AC (50/60Hz). On the PCB are two small switches to set the actuator to AC or DC. The default setting is DC. Before using AC power supply, the switches on the PCB need to be adjusted first. Only use the correct power supply to prevent damage to the actuator. The actuator draws 0.2A nominally, and 1.2A at maximum torque. The actuator has 3 point control. Terminal 1 (minus) and 2 (plus) are permanently connected. Terminal 3 and 4 are control wires. Connecting one of the control wires to the minus, opens or closes the valve. Never connect both control wires at the same time to prevent short circuit and damage to the actuator. To connect the wiring to the actuator, the cover needs to be removed with four bolts. The acatuator has two internal limit switches. As soon as the end position is reached (0 or 90 degrees), the motor is switched off and no energy is consumed. Furthermore, the actuator has two extra limit switches that can be used for position feedback. If required, the angular position can be adjusted. Always connect to the ground, don't use the piping as earthing.
Electrical wiring diagram of the AG-020-B actuator. Before using alternating current, first the switches on the PCB need te be set.
Make sure that the position of the ball and the actuator are properly set before assembly. The actuator is provided with two adapters to connect the actuator to the valve shaft. Mount the actuator to the valve with the provided bolts. There should be no play between both flanges. Use fittings for the connection between the pipe and the valve.
|Max pres (bar)||32|
|Max temp (°C)||130|